KST – KROMSCHRÖDER SYSTEM TECHNOLOGY
Gas max. high gas pressure protection device (SIL 2, PL d)
The Gas max. high gas pressure protection device described in EN 746-2:2010 subclause 18.104.22.168.2.2 is designed to monitor the static gas pressure during the burner start and the burner operation of the system. If the level exceeds the set limit value, the system must perform a fault lock-out.
CO formation due to excess gas → explosion
Determining the required SIL pursuant to IEC 62061
Frequency & exposure duration Fr: < 1 per h to ≥ 1 per day; > 10 min → 5 points
Probability Pr: as the maximum gas pressure is controlled by a pressure regulator and safeguarded by a safety shut-off valve, the probability that a hazardous event occurs is rather low. → 2 points
Avoidance Av: the hazard can be avoided by regular maintenance and the use of an SSV and RV. → 3 points
Effects: death, loss of an eye or arm
Determining the required PL pursuant to ISO 13849-1
Severity of injury S: severe (usually irreversible injury including death) → S2
Frequency and/or duration of hazard exposure F: frequent to continuous and/or long exposure to hazard → F2
Possibility of avoiding hazard or limiting harm P: possible under certain conditions → P1
The required SIL and PL can be achieved with these products. The calculation (see below) provides verification of this.
Sensor: pressure switch for gas DG
Logic: protective system control FCU
Actuator: solenoid valves for gas VAS
The flowchart shows how the products are integrated into the application to achieve the required safely level.
Calculating the SIL, PL
Select products in the adjacent “app”. Depending on the product click on whether the function should have one or two channels and enter the demand rate per hour or per year.