KST – KROMSCHRÖDER SYSTEM TECHNOLOGY
|No.||Component description||Standards and Docuthek|
|010-020||Pressure gauge, e.g. pressure gauge with capsule element KFM with pressure gauge valve DH or MH||Docuthek|
|030||3/2-way valve for checking air deficiency cut-out contact changeover|
|040||Air deficiency cut-out, e.g. pressure switch DG||220.127.116.11.1 Air|
|050||Air flow detector, e.g. pressure switch DG as differential pressure switch||18.104.22.168.1 Air|
|060||Air orifice, e.g. Type VMO for air flow monitoring with differential pressure switch||Docuthek|
Central combustion air supply with air deficiency cut-out and air flow monitoring
The supply air pressure generated by the upstream fan is monitored by the pressure switch (040) acting as an air deficiency cut-out. When the heating system is started by the process control system, the 3/2-way valve (030) is actuated in order to check the contact changeover at the pressure switch.
During the pre-purge, a differential pressure switch (050) monitors the air flow on the orifice (060).
– EN 746-2 recommends that the intake filter on the fan be monitored for soiling. This can occur directly through a differential pressure switch on the filter or indirectly through a second air pressure switch on the pressure side of the fan. The filter monitoring pressure switch triggers a warning, however it does not need to be linked into the safety interlocks.
– In many cases it is recommended that the combustion air be taken in from outside the production hall so as to extend the cleaning intervals for the intake filter. However, drawing in air from the outside does not do away with the need for an intake filter.