KST – KROMSCHRÖDER SYSTEM TECHNOLOGY
18.104.22.168 Condensate drains
In cases where condensates can create a hazard, means shall be provided at the lowest points of the equipment for draining any condensate. When moist gases are being used, condensate drains of a suitable type shall be installed. Any condensate drains, siphons, etc. shall be in a position such that they can be easily checked. Flammable condensates shall be collected by an appropriate means (e.g. piped into a container).
Valves in condensate drains shall be suitably plugged, capped or blank flanged by metallic parts.
The following chapters are printed with the permission of the DIN Deutsches Institut für Normung e.V. (German Institute for Standardization). For the implementation of the DIN Standard, the version with the most recent issue date is deemed authoritative. This is available from Beuth Verlag GmbH, Burggrafenstrasse 6, 10787 Berlin, Germany.