KST – KROMSCHRÖDER SYSTEM TECHNOLOGY
Start-up of the fuel supply and burner(s)1) shall be possible only when
a) the installed air and fuel gas proving devices (e.g. air flow, gas pressure, system leak tightness check) have been checked to ensure that they are in the correct operating condition for start-up;
b) all relevant interlocks (e.g. burner(s) position, valve(s) position, flue damper(s)) have been proved to be in the correct position.
The following chapters are printed with the permission of the DIN Deutsches Institut für Normung e.V. (German Institute for Standardization). For the implementation of the DIN Standard, the version with the most recent issue date is deemed authoritative. This is available from Beuth Verlag GmbH, Burggrafenstrasse 6, 10787 Berlin, Germany.
Our note on this Standard:
1) Start-up of the heating equipment.