KST – KROMSCHRÖDER SYSTEM TECHNOLOGY
Process Control Systems
Multiple burner system, pilot and main burners, modulating-controlled
|No.||Component description||Standards and Docuthek|
|100||Power supply unit|
|210||Combustion air fan|
|311||Air min. air pressure monitor, e.g. DG|
|321||Gas min. low-pressure cut-off, e.g. pressure switch for gas DG|
|322||Gas max. high gas pressure protection, e.g. pressure switch for gas DG|
|331||Emergency stop/Emergency off/Gas off, e.g. Emergency Stop button NTA|
|332||Overtemperature ϑ max|
|350||Valve proving system, e.g. tightness control TC 1-3
|350||Valve proving system, e.g. tightness control TC 410
|450||Burner control unit BCU 480
The burner control unit is mounted to the burner on site and ensures simple commissioning of the burner system.
|450||Automatic burner control unit PFU 780
Automatic burner control units for monitoring and control of gas burners.
Process control system (PCC) for independent control and continuous temperature control of the individual pilot and main burners in a multiple burner system, ionization-controlled with gas and cold air supply.
The supply voltage is supplied to the control system via the power supply unit (100).
Start-up of the combustion air fan (210) includes the “no flow” state check of the Air min. air pressure monitor (311).
The control block for monitoring the safety limits (300) assumes the safety-related monitoring of the safety limits Air min. air pressure monitor (311), Gas min. low-pressure cut-off (321), Gas max. high gas pressure protection device (322), Emergency stop/Emergency off/Gas off (331) and ϑ max. overtemperature monitor (332).
Once the system has started and all safety limits (300) are present, pre-purging (341) of the thermoprocessing equipment begins and the tightness control (350) checks the automatic shut-off valves. Once pre-purge (341) has been completed and the OK signal has been issued by the tightness control (350), the safety interlocks (shown in yellow) are set and the pilot burners are started by the automatic burner control unit (450). Once the pilot burner flame signal has been received by the associated automatic burner control unit (450), the main burner is started in the ignition position. Each burner is set to the ignition position by a separate valve control system (410). Once the main burner flame signal has been received by the associated automatic burner control unit (450), the burner starts. The temperature controller (530) now takes over the temperature/capacity control of the burner.
A system fault lock-out occurs if
- at least one of the safety limits does not lie within the system operating range
- or the tightness control (350) has detected a leak on the main gas valves or burner valves
- or the automatic burner control unit (450) has detected a burner fault.
The system fault lock-out may only be reset manually.
The safety limits listed refer to a typical item of thermoprocessing equipment. The required safety limits may differ, depending on the system type.
If the automatic shut-off valves of each burner are controlling capacities of over 1200 kW, a tightness control (350) must be fitted in accordance with EN 746-2:2010.
In the diagram, a BCU 480 is shown for the automatic burner control unit (450). If another control unit is used, some signals must be provided by an additional control logic.
The LDS (limit during startup) input of the automatic burner control unit (450) must be implemented by an additional control logic.