KST – KROMSCHRÖDER SYSTEM TECHNOLOGY
126.96.36.199.2 Start fuel flow rate
The energy released during the start-up of the burner(s) shall be limited so that the maximum pressure rise from ignition shall not cause any damage to the IThE (see Table 3).
The start fuel flow rate shall be controlled by a protective system according to 5.7.2 and 5.7.3.
Where the burner is ignited manually (e.g. by means of a lighting torch) and has a burner input rate in excess of 70 kW, it shall be equipped with a means of limiting the start-up gas.
The following chapters are printed with the permission of the DIN Deutsches Institut für Normung e.V. (German Institute for Standardization). For the implementation of the DIN Standard, the version with the most recent issue date is deemed authoritative. This is available from Beuth Verlag GmbH, Burggrafenstrasse 6, 10787 Berlin, Germany.